SEARCH WITHIN CONTENT
Citation Information : International Journal on Smart Sensing and Intelligent Systems. Volume 2, Issue 4, Pages 579-601, DOI: https://doi.org/10.21307/ijssis-2017-369
License : (CC BY-NC-ND 4.0)
Published Online: 03-November-2017
In this paper, a heating and ventilation model VVS-400 from Instrutek, Larvik, Norway is modeled using ARX model structure and linear black-box technique. The conventional PID controller and artificial Fuzzy controller are designed based on the approximated plant model and real plant model. The approximated plant model is estimated using System Identification approach while the real plant model is developed by interfacing the Real-time Windows Target toolbox in Matlab with real VVS-plant by using data acquisition (DAQ) card PCI-1711. An artificial Fuzzy controller approach is incorporated in two ways which are conventional Fuzzy logic controller (FLC) and a replacement of conventional fuzzy controller known as Single input fuzzy logic controller (SIFLC). Simulations and experiment validate the equivalency of both controllers. Results reveal that SIFLC found to be better than FLC due to its less computation time compared to conventional FLC.
 Masato Kahara, T. M., Yoshiaki Kuzuu, Takanori Yamazaki, Yukihiro Hashimoto, Kazuyuki Kamimura, Shigeru Kurosu (2001). "Design and tuning of robust PID conroller for HVAC."
 Desheng Liu, Z. X., Qingjun Shi, and Jingguo Zhou (2009). "Fuzzy Immune PID Temperature Control of HVAC Systems." Springer 2: 1138-1144.
 Ming He, W.-J. C., Shao-Yuan Li (2005). "Multiple fuzzy model-based temperature predictive control for HVAC systems." Information Science An International Journal(169): 155-174.
 Qiang Bi, W.-J. C., Qing-Guo Wang, Chang-Chieh Hang, Eng-Lock Lee,Yong Sun, Ke-Dian Liu, Yong Zhang, and Biao Zou (2000). "Advanced controller auto-tuning and its application in HVAC systems." Elsevier, Control Engineering Practice(8): 633-644.
 R.Alcala (2005). “ A genetic rule weighting and selection process for fuzzy control of heating, ventilating and air conditioning.” Engineering Applications of Artificial Intelligence (18): 279-296
 B.Tabakova (2008). “ Design and implementation of real-time fuzzy control for thermodynamic plant.” Proceedings of the 9th WSEAS International Conference of Fuzzy Systems: 61-66
 Lennart Anderson, U. J., Karl Henrik Johansson, and Johan Bengtsson "A manual for system identification."
 M. H. Fazalul Rahiman MIEEE, M. N. T. M. a. Y. M. S. (2006). "Black Box Modeling Of Steam Temperature." 4th Student Conference on Research and Development (SCOReD 2006), Shah Alam, Selangor, MALAYSIA
 Barenthin, M. (2006). "On Input Design in System Identification for Control." KTH School of Electrical Engineering,Stockholm, Sweden.
 Instrutek Manual for VVS-400-Heating and Ventilation Plant (1994).
 Robin Mooney, A. O. D. (2006). "A case study in modeling and process control: the control of a pilot scale heating and ventilation system." Conference paper, School of Electrical and Engineering Systems, Dublin Institute of Technology.
 Ljung, L. (2007). "System Identification Toolbox 7 Reference Manual."
 Mohd Hezri Fazalul Rahiman, M., Mohd Nasir Taib, and Yusof Md Salleh "ARX, ARMAX And NNARX Modeling For Essential Oil Extraction System." Universiti Teknologi MARA, Shah Alam, Malaysia,.
 Underwood, C. P. (2000). "Robust control of HVAC plant II: controller design." Building Services Engineering Research and Technology 21(1): 63-71.
 Kevin M. Passino, S. Y. (1998). "Fuzzy Control." Addison-Wesley.
 Kashif (2009). "Intelligent Control of Diving System of an Underwater Vehicle." Master's Thesis of Engineering (Electrical – Mechatronics & Automatic Control), Universiti Teknologi Malaysia.
 Mathworks (1999). "Real-Time Windows Target User's Guide."